Fuse-Switch Disconnector of Hh15 (QSA) -1000 3p
|FOB Price:||US $22.67-1,170.3 / Piece|
|Min. Order:||100 Pieces|
|Min. Order||FOB Price|
|100 Pieces||US $22.67-1,170.3/ Piece|
|Payment Terms:||L/C, T/T|
- Model NO.: HH15
- Structure: Three-column Disconnector
- Operation: Manual
- Number of Poles: Three Pole
- Switching Mode: Double-Throw Type
- Structure of Operating: Manual
- Brand: People
- Trademark: PEOPLE
- Origin: China
- Type: Low-voltage
- Installation: Indoor High-voltage
- Movement Mode: Horizontal Rotary Type
- Run: Turn the Horizontal
- Common Model: Qsa
- Certification: ISO, CE, ISO9001
- Rated Operate Voltage V: 380V,660V
- Specification: CCC, CE, CB
- HS Code: 8536500000
HH15(QSA),HH15A(QA),HH15P(QP),HH15S(QSS),HH15AS(QPS) series fuse-switch disconnector,is double throw transfer type,is applied to distribution circuit and motor circuit that has high short-circuit current,as unfrequently manual operate main switch or total switch. And the QSA series switch can be used to protect circuit against short-circuit.
This product conforms to standard of IEC60947-3 and GB14048.3.
Normal operational conditions and installation conditions
3.1 Temperater: no higher than +40ºC,and no lower than -5ºC,and the day average temperature no higher than +35ºC.
3.2 Altitude: no higher than 2000m
3.3 The relative humidity: no more than 50%,when temperature is +40ºC.The product can withstand higher humidity under lower temperature,max is 90%.
The condensation that happened because of temperature changes should be taken care.
And Installation location should have no exploresion danger, and no gas and conductive dust which can cause corrosion and insulation damage.
3.4 Class of pollution: 3 level
3.6 Installation type: IV.
For more details and information,please contact us with no hesitate
Or visit our website: http://www.chinapeople.com
Main technical parameter
|conventional heating current Ith(A)||63||125||160||250||400||630||800|
|rated operate current Ie(A)||380V/AC-23B||63||125||160||250||400||630||800|
|rated ultimate short-circuit current(kA r.m.s)||50||50||50||50||50||50||50|
|weight(kg,not including handle)||1.6||1.7||4.1||4.5||4.7||14.0||14.5|